Sneak
Peak Video of the |
Download
Over 100Meg of |
a cool casa for killer 2 may 2001 suppose our doggie friend killer lives in phoenix, where it's 93.5 f in august, on average, with an average daily min and max of 81 and 105.9. let's build him a 2'x4'x4' tall r32 doghouse from something like 3 layers of atlas energy shield 1" polyisocyanurate "r7.2" double-foil foamboards (killer is not a green dog) with 3/4" air spaces between them. the heat conductance of walls and roof is then 64ft^2/r32 = 2 btu/h-f. suppose the doghouse is airtight and killer makes no heat of his own. (with extra credit for fixing those details.) let's keep the house at 85 f max and 83 min on an average day and assume the outdoors is 81 f for 6 hours and 93.5 for 12 h and 105.9 for 6 h on that day (like a modified square wave inverter.) so the average indoor temp is about 84 f and the house gathers 18h(97.6-84)2 = 491 btu of heat from the outdoors over 18 hours, with an average 97.6 outdoor temp. let's cool some thermal mass in the house with outdoor air for 6 hours at night and let it warm by 2 f when the house is closed up for 18 h... 2c = 491, so c = 245 btu/f, like 31 gallons of water or 10 ft^3 of rocks. exposed to 81 f air, it needs to cool from 85 to 83 f in 6 hours, ie 83 = 81 + (85-81)exp(-6/rc), so rc = -6/ln(2/4) = 8.7 h max, with min conductance 245/8.7 = 28.3 btu/h-f and surface 28.3/1.5btu/h-f-ft^2 = 18.9 ft^2 in still air and 18.9/245 = 0.077 ft^2-f/btu s/v ratio, like a 10" water pipe or a 3.3' diameter boulder (with 25 btu/f-ft^3 and no internal thermal resistance.) let's stack 32 6"x6"x10" tall 1 gallon plastic milk jugs on 2x8 shelves along one of the 4'x4' walls. with an average 84-81 = 3 f temp difference over 6 hours, we need an h foot chimney and a ft^2 vent area, where 491 = 6hx16.6asqrt(h)3^1.5, according to one empirical formula, ie asqrt(h) = 0.95. h = 4' makes a = 0.47 ft^2, eg a 2"x4' slot at the base of the jug wall with another slot at the top of the opposite wall. the upper slot might have a lightweight one-way plastic film damper over the outside, or we might install a couple of $12 8"x16" automatic foundation vents with opposed springs or a pv panel and a battery and a differential thermostat and a 16.6(0.47)sqrt(4'x3f) = 27 cfm fan. nick |