re: question about a solar chimney to move air through a greenhouse (techy
12 may 2004
mark & shauna wrote re:
>...what kind of air flow one could expect to achieve using a
>solar chimney of sorts in place of large fans in a greenhouse?
cfm = 16.6asqrt(hdt), with vent area a ft^2 at top and bottom and height
difference h in feet and temp diff dt (f). for instance, on a 70 f day,
a 10' tall 80 f greenhouse with a 100 ft^2 slot at the bottom and a
100 ft^2 slot at the peak would have 16.6(100)sqrt(10x(80-70)) = 16.6k
cfm of airflow.
>the situation is, we are off grid and have a couple decent size
>greenhouses which to date have been using simple vents for cooling and
>air flow. however, we are not getting enough flow which is causing some
>problems. we have actuated vents in the gables at the peak which open at
>a set temperature now but even when full open the air in the greenhouse
>is not moving much on a calm day.
newer plastic film greenhouses and older glass greenhouses have doors
or roll up sides near the ground and a closable slot along the ridge.
>there is no way we can build another power system to drive large enough
>fans so i thought of the solar chimney idea. perhaps an 18"x18" i.d.
>chimney of a given height, black on the outside, etc. i am wondering
>what kind of flow we could achieve on an average sunny day via this
>method. any guesses?
...18"x18" sounds small. a 20'x100' greenhouse might collect 0.8x20x100x250
= 400k btu/h in full sun (or 40% of that under 60% shadecloth.) ignoring
latent heat (and the overwatering that requires), keeping the greenhouse only
10 f warmer than outdoor air requires 400k = 16.6asqrt(10)10^1.5, ie a
= 241 ft^2 vents, eg 2 100'x2' roll up sides and a 3' slot along the ridge.
tired of iraq? do something about it. learn to halve your energy use
while having fun with math and science...
join solar guru steve baer and phd rich komp and pe drew gillett and
me for an all-day workshop on solar house heating and natural cooling
strategies ("hvac nonsense") on july 9 in portland, or--see page 25 of