re: geothermal driveway heating
9 oct 2004
dean carpenter wrote:
>a friend is in construction of his house right now, and plans to install a
>home-grown geothermal heating system in the driveway to keep snow off...
>basically, he's planning on putting down pex (i think ?) tubing before the
>asphalt is laid down, so it's embedded in the asphalt. that will lead to
>several loops dug down below the frost line for heat transfer... it's a
>closed loop system, with a small pump to move the glycol solution through.
>he hasn't done any calculations at all, just "it should work" :) it sounds
>like it will, but i don't know how to calculate if it will or not.
sounds like this could work in principle, but it might require
a lot of water pumping and tubing. you can find some clues here:
they describe a japanese system in which 60 f water circulates through
a heat exchanger under a sidewalk, melts off snow, cools to 45 f, then
gets sprinkled onto the road next to the sidewalk.
and a $3 million swiss system that melts snow off a 14k ft^2 bridge by
storing about 20% of the summer's heat (512k million btu) from tubing
below the asphalt surface in about 2 million ft^3 of sandstone via 91
200' boreholes with heat exchangers :-) the store loses 35% of the heat
by wintertime, when the rest is recovered to melt snow off the bridge.
it looks like most snow melting systems aim at 100 btu/h-ft^2 min, enough
to melt about 1" of snow per hour. you might sprinkle the driveway and
collect water it in a trench along each side. a few leaks might help,
since the main mechanism for upwards heatflow in soil is evaporation
from lower soil layers, upward vapor migration through pores, and
condensation in layers above.